Jacksonville Heating and Air Conditioning Logs
Date: February 10, 2021
Zip Code: 32207
City: Jacksonville, FL
HVAC Technician Notes
Found system was frozen on arrival. Thawed unit. Checked pressures and found the system low on charge. We added a pound and a half of 410A to correct the charge. Tightened all fittings and performed a leak search. We found that the system was leaking at the bottom left corner of the evaporator coil system. We will need a new evaporator coil. The job consisted of two workers and took four hours to complete.