Jacksonville Heating and Air Conditioning Logs
Date: February 10, 2021
Zip Code: 32082
City: Ponte Verda Beach, FL
HVAC Technician Notes
Clean coils drain line change filters check blower motor and heat strip function right side offices heat strips were not working traced issue to a bad double stack sequencer. Replaced sequencer, checked heat strip function, heat strips are back up and running at this time both systems are operating as they should; checked over condensers their straight cool units too cold to really be running in cooling everything’s working as it should.