Jacksonville Heating and Air Conditioning Logs
Date: February 10, 2021
Zip Code: 32259
City: Saint Johns, FL
HVAC Technician Notes
The customer had concerns about one of the AC units not working properly. After gaining access to the roof, found RTU number one, compressor B was running backward. Swap two legs of power to get the compressor unlocked; pumping again. Then phased compressor back properly. After that ran 30-40 minutes and monitored. Compressor ran with no more problems. Also, power cycled the unit to see if it would happen again and it did not. The unit is working properly at this time.